Cause & Consequence
- Moving, flying or falling object
Modification of plant/structures
Incident Info Source
Marine Safety Forum
Specific Incident Equipment
Chemical Tank PRV
Initial and further investigation revealed that the valve must have been subject to unauthorised removal and replacement, during which it had been cross-threaded thereby weakening the connection sufficiently to allow it to loosen and fall.
The valve is only meant to be removed during periodic inspection by a qualified inspector.
The investigation also revealed that it was difficult if not impossible for the quayside gantry to have spotted the fault.
The Supplier is adding an extra visual check to their procedure and is investigating ways to either isolate the valves or physically mark them as only to be removed by qualified inspectors.
Rate this alert
Latest Alerts & Moments
Our searchable catalogue of hundreds of Safety Alerts and Safety Moments are all designed as learning resources that can help improve workplace safety.