Cause & Consequence
- Uncontrolled release of a flammable gas or liquid
Specific Incident Equipment
Gas Distribution GC: Fuel Gas/Blanket (FG) – HP fuel has filter separator pipe work
Lagging around pipe work when removed was found to be damp in places and evidence of corrosion under insulation has taken place. Damage to the insulation was the cause of the moisture ingress.
Section of line repaired.